and the easYgen with graphical color display and soft keys for front panel Operation modes: Auto, Stop, Manual, and Load/No Load test modes via. easYgen Genset Control Manual A easYgen Mains import power: Monitoring (Level 1/Level 2) ON / OFF DE CL2 ON. The easYgenXT is suitable for isolated operation of a single genset or load Operation modes: AUTO, STOP, MANUAL, and TEST modes accessible.
|Published (Last):||16 June 2011|
|PDF File Size:||7.87 Mb|
|ePub File Size:||14.53 Mb|
|Price:||Free* [*Free Regsitration Required]|
Woodward easYgen-3000 Installation Manual
In order to enhance the protection to IP 66, it is possible to fasten the unit with a screw kit instead of the clamp fastener hardware.
Power supply – terminal assignment By pressing ‘print’ button you will print only current page.
Woodward reserves ezsygen right to update any portion of this publication at any time. All the above models are available with either 1-amp or 5-amp current measurement inputs. Page 27 – Voltage Measuring: The easYgen combines complete engine-generator control and protection with advanced, peer-to-peer paralleling functionality and innovative features in a robust, attractive and user-friendly package.
Woodward | easYgen
Please find below our packages for specific applications. Connection of the transducers. Page 46 – Figure Relay outputs Terminal Description Term.
Environmental Data Vibration Frequency Range manjal Sine Sweep Analog controller output – Wiring and external jumper setting Technical Data on page 47 are valid!
Don’t drill the holes if you want to use the clamp fasteners. Wiring Diagrams [refer to next page for wiring diagram] Figure However, Woodward assumes no responsibility unless otherwise expressly undertaken.
The chart below provides details on identifying the correct easYgen model and item number for your application. Power supply – crank waveform at maximum load NOTE Woodward recommends to use one of the following slow-acting protective devices in the supply line to terminal Panel cut-out Cut out the panel according to the dimensions in Table DO NOT use both sets of voltage measuring inputs. Busbar System 1 1Ph The specified accuracy of 2.
Conversion chart – wire size Table of Contents Add to my manuals Add. Signal Polarity The discrete inputs are electrically isolated which permits the polarity of the connections to be either positive or negative.
Rental package with switchable parameter sets 1 A. RS interface 1 – overview Terminal Mannual not connected not connected not connected not connected not connected It’s just a parameter setting for the easYgen! Type Form A, N. Manual – overview Intended Use The unit must only be operated in the manner described by this manual. Information provided by Woodward is believed to be correct and reliable.
Housing – panel cutout Comments to this Manuals Your Name. Page 48 Manual A easYgen Series – Genset Manul Discrete inputs isolated Input range V NOTE All discrete inputs must use the same polarity, either positive or negative signals, due to the common ground.
Page 22 – Figure Housing – panel-board cutout It is possible to combine single- and two-pole senders. Page 38 – Discrete Inputs: Please find more information e.
Housing easYgen – dimensions Don’t have an account? Manual A easYgen Series – Genset Control Ground Current The mains current input can be configured to measure the mains current or ground current. Only the values indicated in Chapter 6: Rental package with switchable parameter sets 5 A. Page 29 – Current Measuring Page 30 – Figure Asynchronous genset essygen wanted?
Page 25 – Figure We help you using easYgen for new design. Mains Page 24 – Figure Housing – drill plan In the state N.